Note: The Green Core Product Identity of the ICF series will be phased in starting March 1, 2015. During the product transition period, you may still receive products that use the previous panel design. Please click here to learn more about Moxa’s Green Core product transition.
Features and Benefits
- Fiber cable test function validates fiber communication
- Auto baudrate detection and data speed up to 12 Mbps
- PROFIBUS bus fail prevents corrupted datagram in functioning segment
- Fiber inverse feature
- Alarm by relay output
- 2 kV galvanic isolation protection
- Dual power inputs for redundancy (Reverse power protection)
- Extends PROFIBUS transmission distance up to 45 km
- Wide temperature model available for -40 to 75°C environments
- Supports Fiber Signal Intensity Diagnosis
The ICF-1180I series industrial PROFIBUS-to-fiber converters are used to convert PROFIBUS signals from copper to optical fiber. The converters are used to extend serial transmission up to 4 km (multi-mode fiber) or up to 45 km (single-mode fiber). The ICF-1180I
provides 2 kV isolation protection for the PROFIBUS system and dual power inputs to ensure that your PROFIBUS device will perform uninterrupted.
Fiber Cable Test Function
Fiber-optic cables are usually deployed for long distance communication. To ensure proper communication across the fiber-optic cables, engineers use fiber sensors. With fiber cable test function through DIP switch adjustments, the ICF-1180I series converters eliminate the need to rely on fiber-optic sensors. This function not only detects fiber communication abnormalities but also validates the format of the received packet. It can also determine which side (Tx or Rx) is causing the problem.
PROFIBUS Fail Safe
When the PROFIBUS device malfunctions or the serial interface fails, it will generate electrical noise, resulting in bus failure. Traditional media converters will let the noise signal pass through the fiber and on to the other converter. This will disrupt data transmissions between the two buses and eventually communication ceases across the entire system. When this occurs, the engineer will not be able to easily locate the failed device because the entire PROFIBUS network is down. To avoid this situation, the ICF-1180I was designed to detect and recognize noise signals. If the bus fails on one side, the noise signal will not propagate through the ICF-1180I and affect additional bus segments. In addition, the ICF-1180I will also trigger an alarm notification to the field engineer on the location of the failure.
Fiber Signal Intensity Diagnosis
In some circumstances, you may need to measure the receive level of the fiber optic port with a voltmeter, which can be connected while the device is operating (doing so will not affect data transmission). The measurement can be taken with a voltmeter and read on a PLC that uses floating high impedance analog inputs, which allows you to do the following: 1. Record the incoming optical power for later measurement (e.g., to indicate aging or damage). 2. Carry out a good/bad test (limit value).
To request a quote, indicate which items you are interested
in below and click "Get a Quote".
||PROFIBUS to fiber converter, multi-mode, ST connector, 0 to 60°C
||PROFIBUS to fiber converter, single-mode, ST connector, 0 to 60°C
||PROFIBUS to fiber converter, multi-mode, ST connector, -40 to 75°C
||PROFIBUS to fiber converter, single-mode, ST connector, -40 to 75°C